Ethanol Equipment Options
Equipment Compatibility and Availability
All existing tank and many associated UST equipment manufacturers have prepared letters stating compatibility to meet federal code.
A service station consists of many interconnected pieces of refueling equipment necessary to fuel vehicles effectively and safely, including approximately 60 pieces of equipment designed to handle fuel and fuel vapor. The equipment that delivers fuel to a vehicle includes tanks, pipes, a submersible turbine pump, a dispenser, and hanging hardware. The remainder and majority of the service station refueling equipment is used to receive and store fuel and prevent, detect, and contain releases. This equipment includes an overfill protection device, a leak detection device, shear valves, fill and vapor caps and adaptors, containment sumps, and all associated fittings and accessories. Equipment that is compatible for use with ethanol blends above E10 is available in every category from multiple manufacturers. Above ground equipment must be UL listed for the fuel dispensed. Below-ground equipment, which must be compliant with federal code, must either be UL listed for the fuel it dispenses or must have a letter from the manufacturer stating its compatibility with specific ethanol content. See the Handbook for Handling, Storing, and Dispensing E85 and Other Ethanol-Gasoline Blends for lists of compatible equipment and information about how to dispense blends above E10 at a station. If specific equipment is not listed, please contact the manufacturer directly as they regularly introduce and retire product lines and models.
Several configurations of tanks exist for storing fuel at stations, including ethanol blends. These include:
Underground Tanks: Most existing tanks are compatible with ethanol blends up to 100%. All existing companies that manufacture steel tanks to store transportation fuels have issued signed letters stating their compatibility to store ethanol blends up to E100, making them compliant with federal code. All steel tank manufacturers have a UL 58 listing for flammable fuels, which includes all transportation fuels. Fiberglass tank compatibility depends on the manufacturer, the year the tank was built, and the type of tank (single or double wall). Both existing fiberglass tank companies, Xerxes and Containment Solutions, have maintained a UL Standard 1316 listing for E100 for many years. Containment Solutions issued a letter stating that all tanks it has manufactured are compatible all ethanol blends. Xerxes and Owens Corning (which no longer manufactures tanks) have stated that compatibility depends on the tank wall type and the year it was manufactured. For more information, refer to Appendix A in the Handbook for Handling, Storing, and Dispensing E85 and Other Ethanol-Gasoline Blends.
Above-Ground Tanks: Above-ground tank manufacturers have also provided statements of compatibility with all ethanol blends including E85.
Tank Preparation: With an above or underground tank, it must be cleaned prior to storing any blend above E10, including E85. E85 will "clean out" and absorb contamination left behind by years of petroleum fuel storage. Converting diesel equipment might require more thorough cleaning. Incompatible tanks need to be replaced.
Other Underground Storage Tank Equipment
All existing pipe manufacturers have UL 971 listing for ethanol blends up to E100. To comply with federal code, other underground equipment manufacturers have either UL listed their equipment up to E85 or have stated approval in writing for specific model types with blends above E10. Other underground equipment includes overfill protection, leak detection, shear valves, fill and vapor caps, adaptors, containment sumps, and all associated fittings and accessories. For other underground storage equipment compatibility, please refer to Appendix B of the Handbook for Handling, Storing, and Dispensing E85 and Other Ethanol-Gasoline Blends.
Above Ground Dispensing Equipment
There are multiple dispenser options for blends above E10 including UL listed E25 and E85 dispensers with blender pump options.
Hanging hardware includes hoses, nozzles, breakaways, and swivels. Both Husky and OPW offer UL listed E25 and E85 nozzles, swivels, and breakaways. Veyance offers UL listed E25 and E85 hose.
Shear valves are an important piece of safety equipment that stop the flow of fuel from the underground storage tank to the dispenser. They prevent fuel release in the event of an accident dislodging the dispenser or a fire. UL listed E85 shear valves are available from Franklin Fueling and OPW.
Submersible turbine pumps draw fuel from the tank and into the piping that delivers the fuel to the dispenser. Both Veeder-Root and Franklin Fueling offer UL listed E85 pumps.
As of July 2015, Wayne no longer offers a conventional E10 dispenser—their standard dispenser is UL listed for E25. Wayne also offers E85 dispensers as an option on multiple models. Gilbarco offers both UL listed E25 and E85 dispensers, and Bennett offers UL listed E85 dispensers.
For lists of UL E10+ listed dispensers, hanging hardware, shear valves, and submersible turbine pumps, please refer to Appendix C of the Handbook for Handling, Storing, and Dispensing E85 and Other Ethanol-Gasoline Blends.